The DiUse System meets the essential safety and health requirements of the European Union. This means that DiUse can be operated and maintained safely if all safety precautions are taken into account. However, dangerous situations can occur due to injudicious or negligent use of the system. The following warning symbol is placed on the DiUse System, underneath the flat cover: Safety
General Information This document provides information on on how to start up a PoU CapDI system, DiUse. All electrical components of the DiUse System are enclosed in the electrical cabinet.
Electrical Hazard: located on the front door and inside the electrical cabinet. The electrical cabinet may never be opened when the system is connected to an electrical outlet.
Cut the box away to gain access to the DiUse System.
Connect to power through the side power connection. Turn the switch on to power the system.
Use 3/8" tubing to connect the push-in fittings to 3 bar (43 PSI) inlet, atmospheric pressure waste and pressurized outlet lines.
Remove one M8 nut per terminal. Slide cable ring onto each terminal, matching red to red. Add the M8 back on top of ring. Tighten using two size 13 spanners.
Unscrew the bolts holding the curved cover in place. Place the module inside the unit, with the red terminal on the left and black on the right.
Connect the "inlet" tube to the single module connection. Connect the remaining two to the central connections.
Edit Purified Conductivity
From the main screen, press down 6 times and then press enter to enable editing. Value is saved on final digit when enter is pressed.
Once the pressure after the system drops below 3.5 bar (51 PSI), the system will automatically start producing water.
Using the LCD, press down to User Functions. Press enter twice to start flush. Advised to flush for 5-10 minutes.
Press ESC to return to main screen. Press enter twice to put the system in operation mode.
If In Doubt, Call Us! If you are unsure on a step or encountering problems, Voltea will be happy to help. Please contact us at+1(496) 620-0133 or at firstname.lastname@example.org
To add a SIM card for data acquisition and alarms:
1.Remove the flat cover panel 2.Open electrical cabinet 3.SIM holder is located center-left on PCB 4.Slide holder down and hinge open
5.Insert SIM 6.Close and slide back up to lock 7.Close cabinet and cover 8.System will auto check for SIM
All rights reserved. No part of this publication may be reproduced, stored in a database or retrieval system, published in any form or in any way, electronically, mechanically, by print, photo print, microfilm or any other means without prior written permission from the manufacturer. All Voltea trademarks and logos are owned by Voltea B.V. All other brand or product names are trademarks or registered marks of their respective owners. Because we are continuously improving our products and services, Voltea reserves the right to change specifications without prior notice. Voltea is an equal opportunity employer. DiUse Start-Up Guide: Copyright © 2017
Made with FlippingBook HTML5