WARNING- RISK OF FIRE:
• Do not operate with flue draft exceeding .08 water column inches (19.9 Pa). • Do not operate with fuel loading or ash removal doors open. • Do not store fuel or other combustible materials within marked installation clearances. • Inspect and clean flues and chimney regularly. DANGER: Risk of Fire and Explosion. Do not burn garbage, gasoline, naphtha, engine oil, or other flammable liquids/inappropriate materials. WARNING: • NEVER use galvanized pipe in your chimney connection, it produces poisonous gases when subjected to extreme temperatures. • USE only lined masonry or manufactured Class “A” HT2100 All Fuel Chimney for your furnace. • INSPECT chimney system periodically for structural integrity. • CLEAN the chimney system regularly to prevent creosote accumulation. • NEVER leave the ash pan in your furnace during operation. • DO NOT CONNECT THIS UNIT TO A CHIMNEY FLUE SERVING ANOTHER APPLIANCE. Duct Runs
• DO NOT USE DUCT ELBOWS HAVING AN INSIDE RADIUS OF LESS THAN 6 inches (150mm) ON OIL, ELECTRIC, OR GAS FURNACES. • DO NOT CONNECT TO A DOWNFLOW FURNACE. • DO NOT CONNECT DUCTWORK SO THAT A REVERSE FLOW IS POSSIBLE. • OPERATE THE GAS/OIL/ELECTRIC/ FURNACE PERIODICALLY TO ENSURE THAT IT WILL OPERATE SATISFACTORILY WHEN NEEDED. • CERTIFIED FOR INSTALLATION WITH APPROPRIATE DUCTWORK CONFIGURATIONS ONLY. • DO NOT RELOCATE OR BYPASS ANY OF THE SAFETY CONTROLS IN THE ORIGINAL GAS/OIL/ELECTRIC FURNACE INSTALLATION. • DO NOT CONNECT TO ANY GAS FURNACE THAT HAS NOT BEEN CERTIFIED INITIALLY AS COMPLYING WITH CAN/CGA-2.3. • THE OPERATION OF THE GAS FURNACE MUST BE VERIFIED FOR ACCEPTABLE OPERATION BEFORE AND AFTER INSTALLATION OF THE ADD-ON APPLIANCE BY A GAS FITTER WHO IS RECOGNIZED BY THE REGULATORY AUTHORITY. • DO NOT CONNECT TO ANY GAS FURNACE THAT IS NOT EQUIPPED WITH AN AIR-CIRCULATION BLOWER, OR TO A CHIMNEY OR VENT SERVICING A GAS FURNACE OR GAS APPLIANCE. The add-on unit should only be installed on a furnace duct system and chimney that are in good operating condition. If exhaust fans are installed in the storage area they should not create negative pressures in the room where the solid fuel-burning appliance is located.
Made with FlippingBook - professional solution for displaying marketing and sales documents online