Be prepared for 18th Edition updates GARY PARKER, ECA SENIOR TECHNICAL MANAGER TELLS YOU WHAT YOU NEED TO KNOW ABOUT AMENDMENT 2 TO THE WIRING REGULATIONS…
T here have been major events and changes since the release of the 18th Edition Wiring Regulations. Since the ubiquitous ‘blue book’ was published in 2018, the electrical contracting industry has encountered Brexit, Covid-19 and material shortages, Building Safety legislation and various green technology and other opportunities. Some of these have shaped the way we look at and think about electrical installations today. On March 28, 2022, the second Amendment to the 18th Edition was released. The new book (brown this time) is filled with important updates that electrical contractors need to know about.
RCD risk assessments These updated requirements relate to Regulation 411.3.3 – RCDs and socket outlets. Previous Editions allowed building owners to omit RCDs in some cases where a risk assessment had been done. This is still an option, but the requirements have been tightened up. Amendment 2 now insists that an RCD must be provided where children or disabled persons are present, regardless of whether a risk assessment has been done.
accordance with the Electricity Safety, Quality and Continuity Regulations (ESQCR), it shall be deemed that the connection between earth and neutral is permeant. Arc fault detection devices AFDDs are now mandatory for circuits supplying socket-outlets with a rated
current not exceeding 32 A in: •Higher risk residential buildings (HRRBs)
•Homes in multiple occupation (HMOs) •Purpose built student accommodation •Care homes This clarifies the specific locations where AFDDs are required. Of course, this does not restrict their uses in other locations. That is up to the designer, but it is worth noting that some limitations do remain regarding AFDDs. For instance, they are single-phase only and may require a minimum load to function correctly.
Further Amendment 2 updates to be aware of: • Protected escape routes • Protection against overvoltages • Bonding of outbuildings • Solar PV systems • Prosumer electrical installations • Certification
Here we shall look at a few of the major changes in BS 7671:2018+A2:2022 (from now, referred to as Amendment 2). Implementation and information The last update to the Wiring
Additional earth electrodes Some new wording has been added to Regulation 411.4.2 recommending that an additional connection to earth, by means of an electrode, is provided to PME earthing systems. As mentioned earlier, the word ‘recommended’ is key here. This is just one option, and not mandatory. The existing Regulation 114.1 still remains and says that where a supply is given in
Regulations will be withdrawn on September 27,2022. Any new work from this date must conform to the new Amendment 2. Some of the wording has also been clarified. For example, some readers took the word ‘recommended’ to mean ‘mandatory’. This has been made clearer throughout, and should now be easier to understand.
You can learn much more about AMD2 in an ongoing series of articles, videos and podcasts available at www.ECAtoday.co.uk. To speak to ECA NI and ROI Regional Manager, Alfie Watterson call: +44 (0)28 9147 9527 or email: email@example.com
www.elecmagazine.com FOLLOW US ON:
IRELAND’S ELECTRICAL MAGAZINE | 17
Made with FlippingBook - professional solution for displaying marketing and sales documents online